Dixell technology is leading the way in electronic regulation and control in the fields of refrigeration, air conditioning and heating, and retail. Dedication to. Dixell. Installing and Operating Instructions rel /02/ – cod. or faulty operation send the instrument back to the distributor or to “Dixell s.r.l.” (see. Digital controllers suitable for both heating and cooling applications. • Built in RS for connection to Dixell’s monitoring system. • Temperature control can be .
|Genre:||Health and Food|
|Published (Last):||28 November 2012|
|PDF File Size:||3.94 Mb|
|ePub File Size:||8.42 Mb|
|Price:||Free* [*Free Regsitration Required]|
The Dixell Universal-R can directly replace all of the following controllers for their most typical applications as well as many others not listed.
Configures output Relay 1 to inverse or direct action. PTC input for temperature, mA input for pressure Sets the band width above set point within which the controller will switch the stages on and off.
98473 – Digital Thermometer XR100C 230V
Sets the maximum temperature sensed by the evaporator probe above which the controller stops evaporator fans from running Sets the time delay between the end of defrost and the evaporator fans re-starting. Its aim was to provide a solution to the problem of sourcing a service replacement when there are so many different types of controller being installed as original equipment.
Configures the controller to inverse or direct action. If set to zero, this function is disabled. To omit a particular defrost period, set it to Push SET for 4 secs. Pr2 0 dPO First Defrost after start up Tells the controller whether to do an immediate defrost when the power is switched on or to wait for the normal interval time as set in parameter IdF. Pr2 10 c Pr2 10 c Pr2 15 mins. These industrial and commercial products play an important role in ensuring human comfort and protecting food throughout the cold chain.
Allows or prevents muting of the alarm buzzer and alarm relay. Tells the controller how many stages it is controlling. The filter should be fitted in series to the vac supply to the control or transformer.
All relays turn off. Sets the display to read out in Celsius or Fahrenheit. Click the X to close this notice.
To use them you must press either the left or right hand side of the button as appropriate. Repeat to turn ON again.
Read only — for factory use. During the energy saving cycle, the temperature display will flash. Tells the evaporator fan to either run continuously apart from during defrost or to cycle on and off with the compressor. Parameters in the Visible Menu can now be accessed directly. Sets the lowest temperature to which the customer can adjust Set Point 1 Sets the lowest temperature to which xixel customer can adjust Set Point vixel Sets the highest temperature to which the customer can adjust Set Point 1 Sets the highest temperature to which the customer can adjust Set Point 2 Sets the high temperature alarm level.
They can be used to control multiple stages, compressors, condenser fans, heaters or pumps. If power spikes are likely to occur, fit a Varsities Part no. These industrial and commercial products play an important role in ensuring human comfort and protecting food throughout the cold chain. The start time for each defrost is stored in non dixell memory, so these will not have been lost.
Innovation and efficiency for a better environment Dixell technology is leading the way in electronic regulation and control in the fields xixel refrigeration, air conditioning and heating, and retail.
Pr2 1 Pr2 30 mins. Access all Dixell manuals. Is the setting correct? Can be used to make sure defrosts are not missed in areas with unreliable power supplies.
Dixell XR/// Series Manuals English
Dixell technology is leading the way in electronic regulation and control in the fields of refrigeration, air conditioning and heating, and retail. Sets the current day. Pr2 0 Pr2 15 mins. Sets the initial temperature alarm delay time on start up so avoiding unnecessary alarms while temperatures stabilize.
Output interference If the control is connected to an inductive coil e. If necessary fit an auxiliary relay or contactor of an appropriate rating. Dedication to technological innovation and constant focus on efficiency have driven the development of solutions designed to maximize energy savings.
Noise Filter for Inductive coils – part no.